Originally Posted by jdrocks
no professional electrician ever made up that subpanel, and i'm betting no building inspector ever put his eyes on it.
time to call a licensed electrician, have him check the whole works.
The electrical master just left, one wire was lose on the receptacle, but except for that everything was fine, well at least he did not find any other funky issues.
Ps: pretty sure I will have my 220V welder wire up at last, the guy is great..